Videos of wiring two gfci outlets together Click to view on YouTube20:36How to Install Multiple GFCI Receptacles in the Same Circuit392K viewsYouTube · 5 years agoClick to view on YouTube17:47How to Wire a Double Receptacle with 20 Amp GFCI Weather Resistant Outlets & Cover269K viewsYouTube · 5 years agoClick to view on YouTube19:55How To Wire a Kitchen Circuit With AFCI/GFCI Protection Using the Leviton AFCI/GFCI Outlet173K viewsYouTube · 2 years agoClick to view on YouTube4:59HOW TO INSTALL A GFCI OUTLET201K viewsYouTube · 5 years agoClick to view on YouTube19:35How to Wire a 20 Amp GFCI Receptacle and a Switch for Exterior Use384K viewsYouTube · 5 years agoClick to view on YouTube0:38GFCI Multiple Location Animation5 viewsYouTube · 1 year agoSee more videos of wiring two gfci outlets together How do I properly wire GFCI outlets in parallel? GFCI receptacles have two sets of contacts, line, and load. The Line side of the receptacle is used to power the device, while the load side is used to power other devices down the line. Any device connected to the load side of a GFCI receptacle, will be protected by the GFCI receptacle.GFCI receptacles have two sets of contacts, line , and load . The Line side of the receptacle is used to power the device, while the load si..Best answer · 17This is the correct behavior. You only need 1 GFCI outlet per circuit (assuming it's at the beginning of the line and the rest of the outlets are..11It is possible. You have to ask yourself if that's what you REALLY want; the design of a GFCI outlet is such that it will protect everything "downs..5GFCIs come marked with two sets of terminals. One pair is marked LINE and the other marked load. Typically, you would connect the line voltage to..3Protecting multiple outlets with one GFCI; is it possibleelectrical - Can I install two independent gfci outlets inSee more results Wiring Diagrams for Multiple Receptacle Outlets - Do-it Wiring Multiple Outlets and a GFCI. Here a gfci receptacle is added at the end of a row of duplex receptacles for single-location protection. The first outlet is connected to the source and 2-wire cable runs from box to box. All wires are spliced with a pigtail at the devices to pass current to the next.